The BASstat series of BACnet-compliant wired or wireless communicating thermostats ensure effortless integration into BACnet/IP (Wi-Fi) or BACnet MS/TP (EIA-485) networks. These thermostats are suited for modulated heating, cooling, and ventilation with analog output control in 4-pipe applications such as Fan Coil Units (FCU) or Air Handlers. A configurable control algorithm allows adaptability to the specific application. This adaptive algorithm applied to the modulated valve control saves energy and ensures comfort for the occupants. Three sensing options are available: built-in temperature sensor, input for remote temperature sensor, or temperature override network command from Building Automation System. Occupancy status can be set from thermostat buttons, a wired ESI input, or over the BACnet network. Thermostat buttons are optionally lockable to prevent unauthorized control or configuration changes. Digital display with graphical icons is easy to read and understand.
NOTE: This unit is designed for 4-pipe HVAC systems and not recommended for 2-pipe HVAC systems.
Note: This unit is designed for 4-pipe HVAC systems and not recommended for 2-pipe HVAC systems.
The BASstat's white backlit LCD display is large and easy to read, even from a distance. It incorporates graphical icons to aid visual indication of current state of operation. Several icons indicate parameters such as: Active Mode, Cooling stage 1 or 2, Heating stage 1 or 2, Ventilation Only, Fan Active, Occupied/Unoccupied state, and Clock icon to indicate Short Cycle Delay or Max Cycles per hour active waiting state. These icons are very useful in indicating the thermostat's current state of operation.
Six buttons on the BASstat allow users to manipulate temperature set point, change HVAC modes, turn the thermostat ON/OFF, and more. Pressing the Set and Up/Down buttons can manually toggle the thermostat from occupied/unoccupied modes, where BACnet occupancy command is not an option. All 6 of these buttons are lockable in a configurable manner to prevent unauthorized configuration change. Some or all buttons can be locked for application flexibility, making the stat suitable for applications where limited user control is allowed.
Sometimes the ideal location to install the thermostat is not the ideal location to capture a correct representation of the temperature in the room, either because it is near a draft, exposed to sunlight, directly under a ceiling fan, near exterior doors or close to equipment that create hot or cold air. In that scenario, a remote temperature sensor is available. Featuring an NTC type 3kΩ thermistor, the temperature sensor is directly compatible with any BASstat model.
|BAST-421C-B2||BACnet MS/TP FCU 4-pipe, single-speed Fan, Wired||$150|
|BAST-421C-BW2||BACnet/IP FCU 4-pipe, single-speed Fan, Wi-Fi||$175|
|TAS-THTRAD0I||Room Aero, 3K, with Insulated Pad (Data Sheet)||$8.50|
|BASRT-B||BASrouter BACnet/IP to MS/TP to Ethernet DIN-Rail Mount||$295|
|BASRTLX-B||BASrouterLX High Performance BACnet Router DIN-Rail Mount||$395|
|BASRTLX-B/P||BASrouterLX High Performance BACnet Router Panel Mount||$395|